STRAIGHT THROUGH JOINT AND BONDING EARTING OF HIGH VOLTAGE CABLE
Underground high Voltage Power Cable Jointing, Bonding and Earthing
Straight through Joints
Each cable is to be run in one continuous length except where the run of cable exceeds the normal manufactured lengths. No other straight joints will be permitted unless specifically authorized by the Engineer.
The outer sheath of all joints buried in the ground shall be contained in a glass fiber or similar box filled with compound or other approved method.
The XLPE cable is provided with sectionalisation on the sheaths on every sixth joint or 3 km whichever is less, with links and earthing provided for the earth screen. Normal operation will be with the sheath bonding links closed and the earth link open.
All XLPE joints and terminations shall be carried out under strictly controlled conditions by cable jointers for the XLPE cable manufacture. The joint insulation shall be of the vulcanized type or other approved type.
The installation rates of the joints specified in schedule IV are to include allowance for the complete joint bay installation including excavation civil work jointing earthing and ancillary equipment.
Where the armour wires of plastic insulated cables constitute the earthed metallic shield such wires shall be efficiently bonded across the joint in a approved manner. The electrical resistance of such bonds shall not exceed that of an equal length of the cable armour wires. Suitable care shall be taken to ensure that the bond contacts do not deteriorate in service.
Bonding and Earthing
Surge protection shall be provided at all joints and terminations not permanently connected to earth to limit in induced voltages to (specified limits). The surge limiting device shall limit the peak voltage as specified for a peak current of 10 kA. These devices shall also withstand the specified a c. r. m. s. maximum voltages without injurious heating.
All cable screens, bonding leads earth conductors earth links etc. shall be capable of withstanding the prospective fault current appropriate to the relevant system voltage for 1.0 second without injurious heating, distortion or damage.
The contractor shall install the minimum number of joints in the cable route, consistent with the specification requirements and sound practice.
The tenderer shall state, in Tender, the philosophy of and details of the screen earthing leads and shall route these conductors in a manner such as to minimize or eliminate circulating currents. The contractor shall ensure that the voltage on exposed metalwork or earth conductor arising from ht passage of load or fault current does not constitute a hazard to personnel, livestock or equipment (including building structures etc.) and shall if required by the Engineer, furnish full information and calculations to demonstrate compliance with this clause.
The contractor design of the system shall take into account the requirement that regular testing of insulation integrity will take place. Connections to earth shall therefore be made through bolted links or by other means to the approval of the Engineer, permitting isolation of cable sheaths and all associated insulated conductors for testing purposes.
Cable sheaths joints and terminations and all associated conductors shall be insulated for voltage likely to arise in operation and shall in any case withstand the specified test voltages.
The contractor is to provide earthing and earthing electrodes for all equipment supplied under this contract in accordance with the requirements of the specification and the tender drawings.
Extensible solid copper earth rod electrodes 1220 mm long 16 mm diameter shall be driven tin sufficient number to ensure that the electrode resistance does not exceed 10 ohms for ancillary equipment and 2 ohms at cable sealing ends remote from substation. All earth electrodes shall be electrically bonded together using copper taps 50 mm x 4 mm. The tops of all electrodes shall be at least 500 mm below the surface of the normal reinstated ground level and the joint between the electrode and the copper tape shall be immersed in asphaltic coating.
The cable contractor is to provide and terminate the earthing 50 mm x 4 mm copper tape from the link box at the outdoor sealing ends or the splitter box to the switchyard or substation main earth. Ancillary equipment shall be earthed to the substation main earth by the cable contractor, earth. Ancillary equipment shall be earthed to the substation main earth by the cable contractor.